# ASHRAE Journal - November 2019 - 34

```TECHNICAL FEATURE

Formulas for Cooling
With Exhaust Fans
BY MIRZA M. SHAH, PH.D., P.E., FELLOW/LIFE MEMBER ASHRAE

Exhaust fans drawing outdoor air are widely used for cooling industrial and commercial facilities. Air drawn into the room picks up the room heat before leaving through
the exhaust fans. Examples are electrical rooms, boiler rooms, manufacturing shops,
etc. Consider a room with sensible heat gain H with an exhaust fan with volumetric
ﬂow rate Q. Outside air at temperature TOA enters the room, picks up heat to rise to a
temperature TROOM
M and is exhausted by the fan. Neglecting the moisture in air, which
has very little effect as its quantity is very small, heat balance gives:
TROOM = TOA +

H
C p DROOM
OO Q

(1)

Where DROOM
M is the density of air leaving the room and
Cp is the speciﬁc heat of air. During the analysis and
evaluation of existing systems, it is often required to
ﬁnd the room temperature that will be maintained by
an exhaust system with a ﬁxed ﬂow rate. To calculate
the room temperature TROOM
M with Eq. (1), the density
of air DROOM
is
required.
This
density depends on room
M
temperature, which is unknown. Thus tedious trial and
error calculations are needed. Calculations are often
simpliﬁed by assuming the room air density to be the
same as the outside air density or that at standard conditions. The approximate formula most commonly used
according to ASHRAE Handbook1 is:
H = 1.1 Q (TROOM
M - TOA)
This can result in considerable error if the

(2)

temperature rise in room is large. To enable easy calculation of room temperature without trial and error,
the author has developed the formulas presented here.
Formulas are also given for easier accurate calculation of
required fan capacity.
As most calculations are done at sea level, formulas
for sea level are given below. Their derivation is given
elevations are given in Appendix 2.

Formulas for Room Temperature
In customary I-P units, the formula is:
TROOM =

572TOAQ
572Q − H

(3)

In SI units, the formula is:
TROOM =

0.353TOAQ
0.353Q − H

(4)

These formulas are derived from Eq. (1) by using the

Mirza M. Shah, Ph.D., P.E., is director of Engineering Research Associates. He is active in research, design, and analysis in mechanical engineering, including heat transfer, ﬂuid
ﬂow, HVAC, refrigeration, plumbing, ﬁre protection, energy conservation, and renewable energy systems.
34

ASHRAE JOURNAL

ashrae.org

N O V E M B E R 2 0 19

```

# ASHRAE Journal - November 2019

Contents
ASHRAE Journal - November 2019 - Intro
ASHRAE Journal - November 2019 - Cover1
ASHRAE Journal - November 2019 - Cover2
ASHRAE Journal - November 2019 - 1
ASHRAE Journal - November 2019 - Contents
ASHRAE Journal - November 2019 - 3
ASHRAE Journal - November 2019 - 4
ASHRAE Journal - November 2019 - 5
ASHRAE Journal - November 2019 - 6
ASHRAE Journal - November 2019 - 7
ASHRAE Journal - November 2019 - 8
ASHRAE Journal - November 2019 - 9
ASHRAE Journal - November 2019 - 10
ASHRAE Journal - November 2019 - 11
ASHRAE Journal - November 2019 - 12
ASHRAE Journal - November 2019 - 13
ASHRAE Journal - November 2019 - 14
ASHRAE Journal - November 2019 - 15
ASHRAE Journal - November 2019 - 16
ASHRAE Journal - November 2019 - 17
ASHRAE Journal - November 2019 - 18
ASHRAE Journal - November 2019 - 19
ASHRAE Journal - November 2019 - 20
ASHRAE Journal - November 2019 - 21
ASHRAE Journal - November 2019 - 22
ASHRAE Journal - November 2019 - 23
ASHRAE Journal - November 2019 - 24
ASHRAE Journal - November 2019 - 25
ASHRAE Journal - November 2019 - 26
ASHRAE Journal - November 2019 - 27
ASHRAE Journal - November 2019 - 28
ASHRAE Journal - November 2019 - 29
ASHRAE Journal - November 2019 - 30
ASHRAE Journal - November 2019 - 31
ASHRAE Journal - November 2019 - 32
ASHRAE Journal - November 2019 - 33
ASHRAE Journal - November 2019 - 34
ASHRAE Journal - November 2019 - 35
ASHRAE Journal - November 2019 - 36
ASHRAE Journal - November 2019 - 37
ASHRAE Journal - November 2019 - 38
ASHRAE Journal - November 2019 - 39
ASHRAE Journal - November 2019 - 40
ASHRAE Journal - November 2019 - 41
ASHRAE Journal - November 2019 - 42
ASHRAE Journal - November 2019 - 43
ASHRAE Journal - November 2019 - 44
ASHRAE Journal - November 2019 - 45
ASHRAE Journal - November 2019 - 46
ASHRAE Journal - November 2019 - 47
ASHRAE Journal - November 2019 - 48
ASHRAE Journal - November 2019 - 49
ASHRAE Journal - November 2019 - 50
ASHRAE Journal - November 2019 - 51
ASHRAE Journal - November 2019 - 52
ASHRAE Journal - November 2019 - 53
ASHRAE Journal - November 2019 - 54
ASHRAE Journal - November 2019 - 55
ASHRAE Journal - November 2019 - 56
ASHRAE Journal - November 2019 - 57
ASHRAE Journal - November 2019 - 58
ASHRAE Journal - November 2019 - 59
ASHRAE Journal - November 2019 - 60
ASHRAE Journal - November 2019 - 61
ASHRAE Journal - November 2019 - 62
ASHRAE Journal - November 2019 - 63
ASHRAE Journal - November 2019 - 64
ASHRAE Journal - November 2019 - 65
ASHRAE Journal - November 2019 - 66
ASHRAE Journal - November 2019 - 67
ASHRAE Journal - November 2019 - 68
ASHRAE Journal - November 2019 - 69
ASHRAE Journal - November 2019 - 70
ASHRAE Journal - November 2019 - 71
ASHRAE Journal - November 2019 - 72
ASHRAE Journal - November 2019 - 73
ASHRAE Journal - November 2019 - 74
ASHRAE Journal - November 2019 - 75
ASHRAE Journal - November 2019 - 76
ASHRAE Journal - November 2019 - 77
ASHRAE Journal - November 2019 - 78
ASHRAE Journal - November 2019 - 79
ASHRAE Journal - November 2019 - 80
ASHRAE Journal - November 2019 - 81
ASHRAE Journal - November 2019 - 82
ASHRAE Journal - November 2019 - 83
ASHRAE Journal - November 2019 - 84
ASHRAE Journal - November 2019 - 85
ASHRAE Journal - November 2019 - 86
ASHRAE Journal - November 2019 - 87
ASHRAE Journal - November 2019 - 88
ASHRAE Journal - November 2019 - Cover3
ASHRAE Journal - November 2019 - Cover4
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_VJKSRY
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SDHUTC
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_JPPKRR
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SDLTTH
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_CKLLES
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SLDOX
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_HJETUK
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_OLUHGE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2020october
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2020october_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_ZERDGH
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_QVMNEO
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_RTPOKE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_BBATRE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_STUBMW
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_TPEMPE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_JNMKDS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_FBTTPA
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_WQMMNE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_TVBRYN
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_showguide2020
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_KTUZMA
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_ABEDGD
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201910
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201909
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2019septmeber_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2019september
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201908
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201907
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201906
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201905
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201904
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2019april
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201903
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2019march
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201902
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201901
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_showguide2019
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2018december
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2018november
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2018fall_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2018fall
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2018october
https://www.nxtbook.com/nxtbooks/ashrae/ashraemexico_2018
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201810
https://www.nxtbook.com/nxtbooks/ashrae/ashraeinsights_201806
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201805
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201804
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201803
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201712
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201711
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201710
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2017fall_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2017fall
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201709
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201705
https://www.nxtbook.com/nxtbooks/ashrae/ashrae_meetinginsert_201610
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2016fall_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2016fall
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_acrexindia
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2015summer_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2015summer
https://www.nxtbook.com/nxtbooks/amca/2014summer2
https://www.nxtbook.com/nxtbooks/amca/2014summer
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_acma_2014summer
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201311
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201309
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_acmasupp_2013fall
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201305
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201303
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2013winter
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201211
https://www.nxtbook.com/nxtbooks/ashrae/achr_expo_mexico2012
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201209
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201208_v3
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201208_v2
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2012summer
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201205
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201203
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2012winter
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201111_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201109_v2
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2011summer
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201105
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201103
https://www.nxtbookmedia.com