# ASHRAE Journal - April 2020 - 69

```COLUMN ENGINEERS NOTEBOOK

Note that there is no decoupler,
also known as a common leg. This
ensures minimum pump energy
and maximum chilled water ∆T, as
explained in the case study building
below (See "Case Study-Northern
California University Example:
Tertiary Blending Vs. Series Building
CHW Pump" subhead on Page 74.)
A bypass around the pumps with
a check valve is provided to allow
the plant secondary pumps to meet
building chilled water demand for
buildings close to the plant that have
sufﬁcient differential pressure from
the secondary pumps.
The control logic is to ﬁrst try to
meet ﬂow demand with the plant
secondary pumps and staging on the
building pumps if differential pressure available from the campus distribution is insufﬁcient. The building chilled water pumps shut off if
the lead pump is at minimum speed
for a period of time and building
chilled water differential pressure
is above setpoint, indicating that
the campus secondary chilled water
pumps are providing the required
chilled water differential pressure.
The boosted-secondary pumping example in Figure 2 shows the
building differential pressure sensor in what the author refers to as
the "trim and respond" position.
Locating the building differential
pressure sensor near the discharge
of the building chilled water pumps
provides ﬁrst-cost and operational
beneﬁts by minimizing length of
controls wiring and locating the
sensor in a location that is easily serviceable. The data collected can also
be used to trend the overall building pressure demands, which can
evaluating building demand history.

To efﬁciently operate the building chilled water pumps with the
building differential pressure
sensor in this conﬁguration, it is
essential that a functional "trim
and respond" algorithm5 is used
to actively reset the building differential pressure setpoint. When

FIGURE 1 Pump power equation.

P=(Q)(H )(SG )
3960()
P=Power, Horse Power
Q=Flow, gpm
SG=Speciﬁc Gravity
=Pump Efﬁciency, Decimal

FIGURE 2 Boosted-secondary pumping building connection example with building ∆P sensor in "trim and
respond" position.

VFD

VFD

Campus
CHWS

∆P (Campus

C

C
Btu Meter

Connection)

Campus
CHWR

Building
CHWS

T

∆P (Building
Demand)

C

C

T

Building
CHWR

FM

properly implemented, a "trim and
respond" algorithm uses the differential pressure sensor as a proxy for
building demand, and the physical
location that the sensor is installed
no longer becomes a factor for
determining how low the differential pressure setpoint can be reset to.
Additionally, locating the differential pressure sensor near the building chilled water pumps can reduce
the potential for "lag" between
changes in building demand and
response from the pumps and
enhance the responsiveness of the
system.
Dedicated building pumps can
also provide a margin of operational
resiliency if the campus distribution pumps are unable to or are not
being properly controlled to maintain a positive pressure differential
at the building connection. In this
scenario, a dedicated building pump

FIGURE 3 Waterside heat transfer equation. Note:
conversion coefficients are based on pure water.
Glycol mixtures will need to be corrected for
changes in fluid properties (e.g., specific heat)
based on how much glycol is used.

Q=m×cP×∆T
Q (Btu/h) = 500×gpm×∆T

in a boosted-secondary conﬁguration could be used to "assist" the
campus distribution pumps in overcoming distribution pressure losses
to a limited degree based on available motor horsepower from the
dedicated building pump.

Optimizing Chilled Water ΔT

High temperature differential
between chilled water supply and
return temperatures, ∆T, is desirable for the decreased volumetric
ﬂow rate required to deliver a given
rate of cooling energy. Figure 3 shows
the waterside heat transfer equation

```

# ASHRAE Journal - April 2020

Contents
ASHRAE Journal - April 2020 - Intro
ASHRAE Journal - April 2020 - Cover1
ASHRAE Journal - April 2020 - Cover2
ASHRAE Journal - April 2020 - 1
ASHRAE Journal - April 2020 - Contents
ASHRAE Journal - April 2020 - 3
ASHRAE Journal - April 2020 - 4
ASHRAE Journal - April 2020 - 5
ASHRAE Journal - April 2020 - 6
ASHRAE Journal - April 2020 - 7
ASHRAE Journal - April 2020 - 8
ASHRAE Journal - April 2020 - 9
ASHRAE Journal - April 2020 - 10
ASHRAE Journal - April 2020 - 11
ASHRAE Journal - April 2020 - 12
ASHRAE Journal - April 2020 - 13
ASHRAE Journal - April 2020 - 14
ASHRAE Journal - April 2020 - 15
ASHRAE Journal - April 2020 - 16
ASHRAE Journal - April 2020 - 17
ASHRAE Journal - April 2020 - 18
ASHRAE Journal - April 2020 - 19
ASHRAE Journal - April 2020 - 20
ASHRAE Journal - April 2020 - 21
ASHRAE Journal - April 2020 - 22
ASHRAE Journal - April 2020 - 23
ASHRAE Journal - April 2020 - 24
ASHRAE Journal - April 2020 - 25
ASHRAE Journal - April 2020 - 26
ASHRAE Journal - April 2020 - 27
ASHRAE Journal - April 2020 - 28
ASHRAE Journal - April 2020 - 29
ASHRAE Journal - April 2020 - 30
ASHRAE Journal - April 2020 - 31
ASHRAE Journal - April 2020 - 32
ASHRAE Journal - April 2020 - 33
ASHRAE Journal - April 2020 - 34
ASHRAE Journal - April 2020 - 35
ASHRAE Journal - April 2020 - 36
ASHRAE Journal - April 2020 - 37
ASHRAE Journal - April 2020 - 38
ASHRAE Journal - April 2020 - 39
ASHRAE Journal - April 2020 - 40
ASHRAE Journal - April 2020 - 41
ASHRAE Journal - April 2020 - 42
ASHRAE Journal - April 2020 - 43
ASHRAE Journal - April 2020 - 44
ASHRAE Journal - April 2020 - 45
ASHRAE Journal - April 2020 - 46
ASHRAE Journal - April 2020 - 47
ASHRAE Journal - April 2020 - 48
ASHRAE Journal - April 2020 - 49
ASHRAE Journal - April 2020 - 50
ASHRAE Journal - April 2020 - 51
ASHRAE Journal - April 2020 - 52
ASHRAE Journal - April 2020 - 53
ASHRAE Journal - April 2020 - 54
ASHRAE Journal - April 2020 - 55
ASHRAE Journal - April 2020 - 56
ASHRAE Journal - April 2020 - 57
ASHRAE Journal - April 2020 - 58
ASHRAE Journal - April 2020 - 59
ASHRAE Journal - April 2020 - 60
ASHRAE Journal - April 2020 - 61
ASHRAE Journal - April 2020 - 62
ASHRAE Journal - April 2020 - 63
ASHRAE Journal - April 2020 - 64
ASHRAE Journal - April 2020 - 65
ASHRAE Journal - April 2020 - 66
ASHRAE Journal - April 2020 - 67
ASHRAE Journal - April 2020 - 68
ASHRAE Journal - April 2020 - 69
ASHRAE Journal - April 2020 - 70
ASHRAE Journal - April 2020 - 71
ASHRAE Journal - April 2020 - 72
ASHRAE Journal - April 2020 - 73
ASHRAE Journal - April 2020 - 74
ASHRAE Journal - April 2020 - 75
ASHRAE Journal - April 2020 - 76
ASHRAE Journal - April 2020 - 77
ASHRAE Journal - April 2020 - 78
ASHRAE Journal - April 2020 - 79
ASHRAE Journal - April 2020 - 80
ASHRAE Journal - April 2020 - 81
ASHRAE Journal - April 2020 - 82
ASHRAE Journal - April 2020 - 83
ASHRAE Journal - April 2020 - 84
ASHRAE Journal - April 2020 - 85
ASHRAE Journal - April 2020 - 86
ASHRAE Journal - April 2020 - 87
ASHRAE Journal - April 2020 - 88
ASHRAE Journal - April 2020 - 89
ASHRAE Journal - April 2020 - 90
ASHRAE Journal - April 2020 - 91
ASHRAE Journal - April 2020 - 92
ASHRAE Journal - April 2020 - 93
ASHRAE Journal - April 2020 - 94
ASHRAE Journal - April 2020 - 95
ASHRAE Journal - April 2020 - 96
ASHRAE Journal - April 2020 - Cover3
ASHRAE Journal - April 2020 - Cover4
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_YELQLJ
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_QJLWMC
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_MCDEBX
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_WNYSQY
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_XATVOD
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_FJSHSS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_CCBZDS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_XDEFVG
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2023november_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2023november
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_VHGNBL
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_WPKBNJ
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_UUVCDE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_RTGDEW
https://www.nxtbook.com/nxtbooks/ashrae/ashraemexico_2023
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_LKRFXS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_AZSOFG
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_ERCDBH
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_QWDFRV
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_JHGVDF
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_OPUYHG
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SREIBM
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_LRTGLK
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_OKRFGH
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2022november_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2022november
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_TZSERA
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_LVRUIX
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_RPTVYZ
https://www.nxtbook.com/nxtbooks/ashrae/mini_pub_catalog
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_XIYTGD
https://www.nxtbook.com/nxtbooks/ashrae/ashraemexico_2022
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_RFGDOB
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_PABXNU
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_REMKLS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_PICVBT
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_AOYTVW
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_JQOPLS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_IOYTBC
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SGAJJF
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_IGHYER
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_PDRKLS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2021november
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2021november_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_XCODFR
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_QSLFGO
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_ILKVNM
https://www.nxtbook.com/nxtbooks/ashrae/ashraemexico_2021
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_OPDJKD
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_VJKSRY
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SDHUTC
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_JPPKRR
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SDLTTH
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_CKLLES
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_SLDOX
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_HJETUK
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_OLUHGE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2020october
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2020october_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_ZERDGH
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_QVMNEO
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_RTPOKE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_BBATRE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_STUBMW
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_TPEMPE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_JNMKDS
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_FBTTPA
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_WQMMNE
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_TVBRYN
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_showguide2020
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_KTUZMA
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_ABEDGD
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201910
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201909
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2019septmeber_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2019september
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201908
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201907
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201906
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201905
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201904
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2019april
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201903
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2019march
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201902
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201901
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_showguide2019
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2018december
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2018november
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2018fall_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2018fall
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_2018october
https://www.nxtbook.com/nxtbooks/ashrae/ashraemexico_2018
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201810
https://www.nxtbook.com/nxtbooks/ashrae/ashraeinsights_201806
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201805
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201804
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201803
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201712
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201711
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201710
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2017fall_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2017fall
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201709
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201705
https://www.nxtbook.com/nxtbooks/ashrae/ashrae_meetinginsert_201610
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2016fall_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2016fall
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_acrexindia
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2015summer_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_amca_2015summer
https://www.nxtbook.com/nxtbooks/amca/2014summer2
https://www.nxtbook.com/nxtbooks/amca/2014summer
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_acma_2014summer
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201311
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201309
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_acmasupp_2013fall
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201305
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201303
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2013winter
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201211
https://www.nxtbook.com/nxtbooks/ashrae/achr_expo_mexico2012
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201209
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201208_v3
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201208_v2
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2012summer
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201205
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201203
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2012winter
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201111_v2
https://www.nxtbook.com/nxtbooks/ashrae/ashraejournal_201109_v2
https://www.nxtbook.com/nxtbooks/ashrae/pubcatalog_2011summer
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201105
https://www.nxtbook.com/nxtbooks/ashrae/meetingplanner_201103
https://www.nxtbookmedia.com